HMI Pad › Forums › Main Forums › ScadaMobile Support › Micrologix 1400
This topic contains 2 replies, has 3 voices, and was last updated by djovetta 5 years, 10 months ago. This post has been viewed 2658 times
I've a allen bradley micrologix 1400 (w/ embedded ethernet port). I've tried to configure "scada mobile" to the controller using revised micrologix-one.csv & contrologix-one.csv, w/o success. Works okay w/ modbus-one.csv, as micrologix 1400 supports modbus tcp/ip. Works okay w/ kepware (which i've configured w/ driver = allen bradley contrologix, device = micrologix 1400).
Pls. advise. Thanks.
1. must use the EIP/PCCC validation_tag for ML1400
2. ML1400 is NOT ControlLogix type addressing
3. must use EIP/PCCC protocol
If you have not already got it working,
I will guess the validation tag is issue.
I use; N98:0 = 1400 (578 hex)
The 578 is also entered in iOS device.
Also, I embed the controller IP address on first CSV line.
This at end of first tag row in CSV file;
local_ip:="192.168.1.30"; poll_interval = 0.50;
hope this helps
I’ve tried to configure “scada mobile” to the Micrologix 1400 using revised micrologix-one.csv file.
I got the manage “Validation Failure: SLC/MICROLOGIX Controller reported an error for tag “N98:0″ or did not recognize it . ”
I tried the “1400″ and “578″ on validation code , with no success .
There is another validation code ? how can I Set a new validate code? I did not find any N98 on AB documents .
You must be logged in to reply to this topic.